Precautions for diesel generator sets
1. The rated power (that is, the capacity of the diesel generator set) is the allowable output power for 12 hours of continuous operation under the conditions of an ambient temperature of 20°C, a relative humidity of 60%, and an atmospheric pressure of 760 mm Hg (including 10 overloads). % Run for 1 hour).
When working under the above environmental conditions, the output power of the generator set must be trimmed
2. When the diesel generator set runs continuously for more than 12 hours, it will be converted at 90% of its output power (i.e. permanent power). If the above environmental conditions are exceeded, the permanent power is also calculated as 90% of the corrected power.
3. If the diesel generator set is used in an environment beyond the above 1, 2 and 3, the output power can also be modified according to the diesel engine operation and maintenance manual.